- Cross verify the application configuration and set addresses (Int. Comm. ID Ch-7531) for all units in the system. This requires Laptop/PC for verifying the set Plant application configuration in Application Configuration window using Utility software.
- Check physically CAN wiring and make sure that wires are connected in daisy chain loop and terminal orientation i.e. CAN L & H are interconnected properly.
- Check both CAN ends are terminated with 120 Ω resistor.
CAN alarm/issues: Any DG missing / Any Mains missing/Any BTB missing Print
Modified on: Mon, 22 Aug, 2022 at 8:57 AM
Did you find it helpful? Yes NoSend feedback
Sorry we couldn't be helpful. Help us improve this article with your feedback.